We informed our clients about scheduled service inspection of the first circuit of the central UPS and regular dieselgenerator load test before Christmas. Both operations were successfully completed today with the simply result: excellent!
Within the regular service inspection, all four central modules UPS 70NET 44/33, which ensure backup power for server room S1 and S2 in the event of emergencies, were tested. Along with this revision, the regular load test of dieselgenerator was passed with no evidence of any deviation from standard operation.
Thank you for being with us