We informed you about scheduled service inspection of the second circuit of the central UPS in the second half of March. Revision was scheduled on Tuesday, April 2, 2019 from 8 a.m. to 5 p.m. and successfully completed.
All four central modules EATON 93PM-50, which ensure backup power for server room S3, were entirely checked within the regular service inspection. Thanks to redundancy of these modules, the revision was held without any outage within full operation.
Along with this inspection, the regular load test of dieselgenerator was succesful in the automatic regime as well.
Thank you for being with us